The paper presents a new method for simultaneous tracking of varying grid impedance and its uncertainty bounds. Impedance tracking consists of two stages. In the first stage, the actual noise estimate is obtained from least squares (LS) residua. In the second stage, the noise covariance matrix is approximated with the use of residual information. Then weighted least squares (WLS) method is applied in order to estimate impedance and background voltage. Finally uncertainty bounds for impedance estimation are computed. The robustness of the method has been verified using simulated signals. The proposed method has been compared to sliding LS. The results have shown, that the method performs much better than the LS for all considered cases, even in the presence of significant background voltage variations.
Quality of energy produced in renewable energy systems has to be at the high level specified by respective standards and directives. One of the most important factors affecting quality is the estimation accuracy of grid signal parameters. This paper presents a method of a very fast and accurate amplitude and phase grid signal estimation using the Fast Fourier Transform procedure and maximum decay side-lobes windows. The most important features of the method are elimination of the impact associated with the conjugate’s component on the results and its straightforward implementation. Moreover, the measurement time is very short ‒ even far less than one period of the grid signal. The influence of harmonics on the results is reduced by using a bandpass pre-filter. Even using a 40 dB FIR pre-filter for the grid signal with THD ≈ 38%, SNR ≈ 53 dB and a 20‒30% slow decay exponential drift the maximum estimation errors in a real-time DSP system for 512 samples are approximately 1% for the amplitude and approximately 8.5・10‒2 rad for the phase, respectively. The errors are smaller by several orders of magnitude with using more accurate pre-filters.
The paper investigates a significant influence of transients on steady states in a matrix converter with the one-periodic control strategy. Proposed controller can be used as an interconnection device within a power system for a power flow control. However, the presence of inductances in external systems has the significant influence on steady state of a matrix converter operation. The special current injection method has been developed to ensure a proper operation of a matrix converter. Presented analysis of steady states is carried out in a frequency domain using the harmonic balance method. Obtained numerical results, which are confirmed by a time domain analysis, prove the effectiveness of the proposed method.
The paper presents abilities and advantages following from the use of the harmonicbalance method for analysis of steady state of a multiphase system with switching devices on example of a matrix converter. Switching elements are modelled as resistances with step-wise variable parameters, what allows to describe the converter by a linear infinite set of equations. The analysis in frequency domain is presented on example of the one-periodic control strategy. External systems were also added using the Thevenin method approach. The numerical calculation results of a linear equations set were verified by the variable structure method in a time domain and the numerical convergence was confirmed. Furthermore, the exemplary complex system was analysed using the cascade method and current waveforms were obtained.
The paper deals with frequency estimation methods of sine-wave signals for a few signal cycles and consists of two parts. The first part contains a short overview where analytical error formulae for a signal distorted by noise and harmonics are presented. These formulae are compared with other accurate equations presented previously by the authors which are even more accurate below one cycle in the measurement window. The second part contains a comparison of eight estimation methods (ESPRIT, TLS, Prony LS, a newly developed IpDFT method and four other 3-point IpDFT methods) in respect of calculation time and accuracy for an ideal sine-wave signal, signal distorted by AWGN noise and a signal distorted by harmonics. The number of signal cycles is limited from 0.1 to 3 or 5. The results enable to select the most accurate/ fastest estimation method in various measurement conditions. Parametric methods are more accurate but also much slower than IpDFT methods (up to 3000 times for the number of samples equal to 5000). The presented method is more accurate than other IpDFT methods and much faster than parametric methods, which makes it possible to use it as an alternative, especially in real-time applications.
Fast and accurate grid signal frequency estimation is a very important issue in the control of renewable energy systems. Important factors that influence the estimation accuracy include the A/D converter parameters in the inverter control system. This paper presents the influence of the number of A/D converter bits b, the phase shift of the grid signal relative to the time window, the width of the time window relative to the grid signal period (expressed as a cycle in range (CiR) parameter) and the number of N samples obtained in this window with the A/D converter on the developed estimation method results. An increase in the number b by 8 decreases the estimation error by approximately 256 times. The largest estimation error occurs when the signal module maximum is in the time window center (for small values of CiR) or when the signal value is zero in the time window center (for large values of CiR). In practical applications, the dominant component of the frequency estimation error is the error caused by the quantization noise, and its range is from approximately 8×10-10 to 6×10-4.
This paper presents an analytical model of a three-phase axial flux coreless generator excited by permanent magnets, with special focus on determining the model pa- rameters. An important aspect of this model is the derivation of a coefficient that corrects the flux on the inside and outside edges of the magnets. The obtained parameters are ver- ified by performing field analyses and measurements. A comparison of the results show satisfactory convergence, which confirms the accuracy of the proposed analytical model.