Finding the most critical contingencies in a power system is a difficult task as multiple evaluations of load and generation scenarios are needed. This paper presents a mathematical formulation for selecting, ranking, and grouping the most critical N-1 network contingencies, based on the calculation of a Power Constraint Index (PCI) obtained from the Outage Transfer Distribution Factors (OTDF). The results show that the PCI is only affected by the impedance parameter of the transmission network, the topology, and the location of all generators. Other methods, such as the Performance Index (PI) and the Overload Index (OL) are affected by the power generation and demand variations. The proposed mathematical formulation can be useful to accelerate the calculation of other methods that evaluate contingencies in power system planning and operation. Furthermore, the fast calculation of indices makes it suitable for online evaluation and classification of multiple events considering the current topology. The results showed that the proposed al- gorithm easily selected and ranked the expected contingencies, with the highest values of the index corresponding to the most critical events. In the filtering process, the computa- tional calculation time improved without losing the robustness of the results.
A data logger has been built to record, for a month, the power consumption of various equipment and the temperature at different points inside and outside of a radio communication base station operated by Vodafone Portugal. Here we show how the concerns with measurement uncertainty led us to choose an analog system over a digital one for AC power measurement.
Intensive modernization and reconstruction of the energy sector takes place throughout the world. The EU climate and energy policy will have a huge impact on the development of the energy sector in the coming years. The European Union has adopted ambitious goals of transforming towards a low-carbon economy and the integration of the energy market. In June 2015, the G7 countries announced that they will move away from coal fired energy generation. Germany, which has adopted one of the most ambitious energy transformation programs among all industrialized countries, is leading these transformations. The long-term strategy, which has been implemented for many years, allowed for planning the fundamental transformation of the energy sector; after the Fukushima Daiichi nuclear disaster, Germany opted for a total withdrawal from nuclear energy and coal in favor of renewable energy. The German energy transformation is mainly based on wind and solar energy. Germany is the fifth economic power in the world and the largest economy in Europe. Therefore, the German energy policy affects the energy policy of the neighboring countries. The article presents the main assumptions of the German energy policy (referred to as Energiewende). It also presents the impact of changes in the German energy sector on the development of energy systems in selected European countries.
The paper presents a new method for simultaneous tracking of varying grid impedance and its uncertainty bounds. Impedance tracking consists of two stages. In the first stage, the actual noise estimate is obtained from least squares (LS) residua. In the second stage, the noise covariance matrix is approximated with the use of residual information. Then weighted least squares (WLS) method is applied in order to estimate impedance and background voltage. Finally uncertainty bounds for impedance estimation are computed. The robustness of the method has been verified using simulated signals. The proposed method has been compared to sliding LS. The results have shown, that the method performs much better than the LS for all considered cases, even in the presence of significant background voltage variations.
Fast and accurate grid signal frequency estimation is a very important issue in the control of renewable energy systems. Important factors that influence the estimation accuracy include the A/D converter parameters in the inverter control system. This paper presents the influence of the number of A/D converter bits b, the phase shift of the grid signal relative to the time window, the width of the time window relative to the grid signal period (expressed as a cycle in range (CiR) parameter) and the number of N samples obtained in this window with the A/D converter on the developed estimation method results. An increase in the number b by 8 decreases the estimation error by approximately 256 times. The largest estimation error occurs when the signal module maximum is in the time window center (for small values of CiR) or when the signal value is zero in the time window center (for large values of CiR). In practical applications, the dominant component of the frequency estimation error is the error caused by the quantization noise, and its range is from approximately 8×10-10 to 6×10-4.
The large variability and unpredictability of energy production from photovoltaic power microinstallations results from the dependence on the current weather conditions. These conditions depend on a number of factors and are variable over the time. Despite this specificity, photovoltaic micro-installations are becoming more and more popular in the world and in Poland. This is mainly due to the fact that the generation of energy from renewable sources has numerous advantages, the energy is free, renewable in time and ecological, and its production on its own gives partial independence from energy supplies from the power grid. In addition, the observed significant prices decrease of solar modules has further accelerated the development of the use of this energy source. Concern for this method of energy production among households has increased significantly in Poland after introducing the prosumer in the legal framework and the use of administrative and financial support. The implemented prosumer mechanisms allowed, for example, the net balancing of the energy consumed and produced by the micro-installation through storage in the power grid. The article describes the problem of balancing sources using solar energy, based on micro-installation used in the household (the so-called prosumer installation). The conducted analyses compared the load profile of a typical household and the energy generation profile from a photovoltaic installation, determining the real balancing formation level of such a system.
The paper concerns the assessment of blackout hazards in the power systems. On the basis of statistical data from more than one hundred failures in power systems that affected the world in the last fifty years, the analysis was carried out regarding the number of people affected by a blackout, power losses in the system, duration of a failure and its direct causes. The paper also describes the methodology of risk analysis and vulnerability analysis of the extraordinary events occurrence in electrical power systems resulting in failures. The structure of risk analysis was based on the bow tie model, identifying threats, unwanted events, barriers and consequences of a system failure. Moreover, particular attention was drawn to the impact of the power reserve deficit in the Polish Power System in the coming years on the increase in the risk of a blackout failure.
The paper presents an analysis of the sustainable development of electricity generation sources in the National Power System (NPS). The criteria to be met by sustainable power systems were determined. The paper delineates the power balance of centrally dispatched power generation units (CDPGU), which is required for the secure work of the NPS until 2035. 19 prospective electricity generation technologies were defined. They were divided into the following three groups: system power plants, large and medium combined heat and power (CHP) plants, as well as small power plants and CHP plants (distributed sources). The quantities to characterize the energy effectiveness and CO2 emission of the energy generation technologies analyzed were determined. The unit electricity generation costs, discounted for 2018, including the costs of CO2 emission allowance, were determined for the particular technologies. The roadmap of the sustainable development of the generation sources in the NPS between 2020 and 2035 was proposed. The results of the calculations and analyses were presented in tables and figure
Power systems that are highly loaded, especially by a stochastic supply of renewables and the presence of storages, require dynamic measurements for their optimal control. Phasor measurement units (PMUs) can be used to capture electrical parameters of a power system. Standards on the PMU dynamic performance have been modified to incorporate their new dynamic mode of operation. This paper examines the PMU dynamic performance and proposes essential algorithms for measurement accuracy verification. Measurements of dynamic input signals, which vary in amplitude or frequency, were taken during automated tests of two PMUs. The test results are presented and expounded with further recommendation for the performance requirements. This paper also presents and examines applied testing procedures with relevance to the specifications of the IEEE Standard for Synchrophasor C37.118.1™-2011 and its amendment C37.118.1a™-2014.
A solar photovoltaic (PV) system has been emerging out as one of the greatest potential renewable energy sources and is contributing significantly in the energy sector. The PV system depends upon the solar irradiation and any changes in the incoming solar irradiation will affect badly on the output of the PV system. The solar irradiation is location specific and also the atmospheric conditions in the surroundings of the PV system contribute significantly to its performance. This paper presents the cumulative assessment of the four MPPT techniques during the partial shading conditions (PSCs) for different configurations of the PV array. The partial shading configurations like series-parallel, bridge link, total cross tied and honeycomb structure for an 8#2;4 PV array has been simulated to compare the maximum power point tracking (MPPT) techniques. The MPPT techniques like perturb and observe, incremental conductance, extremum seeking control and a fuzzy logic controller were implemented for different shading patterns. The results related to the maximum power tracked, tracking efficiency of each of the MPPT techniques were presented in order to assess the best MPPT technique and the best configuration of the PV array for yielding the maximum power during the PSCs.
The electrical power drawn by an induction motor is distorted in case of appearance of a certain type of failures. Under spectral analysis of the instantaneous power one obtains the components which are connected with definite types of damage. An analysis of the amplitudes and frequencies of the components allows to recognize the type of fault. The paper presents a metrological analysis of the measurement system used for diagnosis of induction motor bearings, based on the analysis of the instantaneous power. This system was implemented as a set of devices with dedicated software installed on a PC. A number of measurements for uncertainty estimation was carried out. The results of the measurements are presented in the paper. The results of the aforementioned analysis helped to determine the measurement uncertainty which can be expected during bearing diagnostic measurements, by the method relying on measurement and analysis of the instantaneous power of an induction machine.
A sliding mode controller for the photovoltaic pumping system has been proposed in this paper. This system is composed of a photovoltaic generator supplying a three-phase permanent magnet synchronous motor coupled to a centrifugal pump through a three-phase voltage inverter. The objective of this study is to minimise the number of regulators and apply the sliding mode control by exploiting the specification of the field oriented control scheme (FOC). The first regulator is used to force the photovoltaic generator to operate at the maximum power point, while the second is used to provide the field oriented control to improve the system performance.The whole system is analysed and its mathematical model is done. Matlab is used to validate the performance and robustness of the proposed control strategy.
A comparative analysis concerning the influence of different factors on momentum transfer in mechanically agitated systems was carried out on the basis of experimental results for solid-liquid, gas-liquid and gas-solid-liquid systems. The effects of the impeller - baffles system geometry, scale of the agitated vessel, type and number of impellers and their off-bottom clearance, as well as physical properties of the multiphase systems on the critical impeller speeds needed to produce suspension or dispersion, power consumption and gas hold-up were analysed and evaluated.
An analysis of the power system functioning and the behaviors of the energy market participants allows the trends taking place within years to be identified, including these associated with the evolution of the electric energy and power demand profiles. The problems of balancing the peak power demand are of both a short and long term nature, which implies the need for changes in the electricity generation sector. Apart from the existing “silo-type” generation units, the construction of distributed energy sources implemented in the civic formula in the framework of self-sufficient energy communes and energy clusters is becoming increasingly important. Support for these programs is realized both at the legislative level, as well as within dedicated competitions and ministerial activities. The financial support carried out by the National Fund for Environmental Protection and Water Management and the Regional Operational Programs is also noticeable. One of the activities aimed at spreading the idea of clustering was the competition for certified energy clusters, conducted by the Ministry of Energy. The goal of the contest was the promotion and development of the distributed energy sector, which could be used for the improvement of energy security in the local manner and constitute a basis for the knowledge necessary in planning and developing the state’s energy policy. The paper presents a synthetic analysis of the results of the competition for a certified energy cluster from the perspective of planning and operational needs related to the functioning of the power system. Further, the information about the investment plans of new generation capacities, including their breakdown with respect to type, achievable power and costs has been provided. Also, the balancing of the demand for electric energy by own generation within the energy clusters has been characterized for three time perspectives
An electric power steering system (EPS) is a new type of steering system developed after a mechanical hydraulic power system (MHPS) and electric-hydraulic power steering system (EHPS). In order to coordinate and solve the portability and sensitivity of the steering system optimally, taking an induction power steering system as the research object, the control algorithm of induction motor control under the EPS is studied in this paper. In order to eliminate the feed-forward performance degradation caused by the change of feed-forward parameters, an on-line identification algorithm of feed-forward parameters is proposed. It can improve the control performance of online identification among three feed-forward parameters in the T-axle motor, it improves on the robustness of feed-forward control performance, at the same time it also gives simulation and test results. This method can improve the control performance of the three feed-forward parameter online identification of the T-axis motor and improve the robustness of feed-forward control performance. At the same time, simulation and test results are given. The simulation results show that the algorithm can significantly improve the response speed and control accuracy of EPS system control.
Increasing the share of energy production from renewable sources (RES) plays a key role in the sustainable and more competitive development of the energy sector. Among the renewable energy sources, the greatest increase can be observed in the case of solar and wind power generation. It should be noted that RES are an increasingly important elements of the power systems and that their share in energy production will continue to rise. On the other hand the development of variable generation sources (wind and solar energy) poses a serious challenge for power systems as operators of unconventional power plants are unable to provide information about the forecasted production level and the energy generated in a given period is sometimes higher than the demand for energy in all of the power systems. Therefore, with the development of RES, a considerable amount of the generated energy is wasted. The solution is energy storage, which makes it possible to improve the management of power systems. The objective of this article is to present the concept of electricity storage in the form of the chemical energy of hydrogen (Power to Gas) in order to improve the functioning of the power system in Poland. The expected growth in the installed capacity of wind power plants will result in more periods in which excess energy will be produced. In order to avoid wasting large amounts of energy, the introduction of storage systems is necessary. An analysis of the development of wind power plants demonstrates that the Power to Gas concept can be developed in Poland, as indicated by the estimated installed capacity and the potential amount of energy to be generated. In view of the above, the excess electricity will be available for storage in the form of chemical energy of hydrogen, which
In renewable systems, there may be conditions that can be either network error or power transmission line and environmental conditions such as when the wind speed is unbalanced and the wind turbine is connected to the grid. In this case, the control system is not damaged and will remain stable in the power transmission system. Voltage stability studies on an independent wind turbine at fault time and after fixing the error is one of the topics that can strengthen the future of independent collections. At the time of the fault, the network current increases dramatically, resulting in a higher voltage drop. Hence the talk of fast voltage recovery during error and after fixing the error and protection of rotor and grid side converters against the fault current and also protection against rising DC voltage (which sharply increases during error) is highly regarded. So, several improvements have been made to the construction of a doubly-fed induction generator (DFIG) turbine such as: a) error detection system, b) DC link protection, c) crow bar circuit, d) block of the rotor and stator side converters, e) injecting reactive power during error, f) nonlinear control design for turbine blades, g) tuning and harmonization of controllers used to keep up the power quality and to stabilize the system output voltage in the power grid. First, the dynamic models of a wind turbine, gearbox, and DFIG are presented. Then the controllers are modeled. The results of the simulation have been validated in MATLAB/Simulink.
This article presents the main stages and challenges in modelling and designing of modern ultrasonic welding and cutting systems. First, the key components of such a system, such as an ultrasonic stack (con- sisting of a high power ultrasonic transducer and a sonotrode) and a digitally controlled ultrasonic power supply with precise control of the output power, have been considered. Next, a concept of measurement system for verification and validation of mathematical models of ultrasonic stacks and its components has been presented. Finally, a method of ultrasonic stack e-diagnosis based on ultrasonic transducer electrical impedance measurement during welding and cutting process has been described
The uncontrolled power flow in the AC power system caused by renewable energy sources (restless sources, distributed energy sources), dynamic loads, etc., is one of many causes of voltage perturbation, along with others, such as switching effects, faults, and adverse weather conditions. This paper presents a three-phase voltage and power flow controller, based on direct PWM AC/AC converters. The proposed solution is intended to protect sensitive loads against voltage fluctuation and problems with power flow control in an AC power system. In comparison to other solutions, such as DVR, UPFC, the presented solution is based on bipolar matrix choppers and operates without a DC energy storage unit or DC link. The proposed solution is able to compensate 50% voltage sags, in the case of three-phase symmetrical voltage perturbation, and single phase voltage interruptions. Additionally, by means of a voltage phase control with a range of #6;60◦ in each phase, it is possible to control the power flow in an AC power system. The paper presents an operational description, a theoretical analysis based on the averaged state space method and four terminal descriptions, and the experimental test results from a 1 kVA laboratory model operating under active load.
High voltage direct current (HVDC) emergency control can significantly improve the transient stability of an AC/DC interconnected power grid, and is an important measure to reduce the amount of generator and load shedding when the system fails. For the AC/DC interconnected power grid, according to the location of failure, disturbances can be classified into two categories: 1) interconnected system tie-line faults, which will cause the power unbalance at both ends of the AC system, as a result of the generator rotor acceleration at the sending-end grid and the generator rotor deceleration at the receiving-end grid; 2) AC system internal faults, due to the isolation effect of the DC system, only the rotor of the generator in the disturbed area changes, which has little impact on the other end of the grid. In view of the above two different locations of disturbance, auxiliary power and frequency combination control as well as a switch strategy, are proposed in this paper. A four-machine two-area transmission system and a multi-machine AC/DC parallel transmission system were built on the PSCAD platform. The simulation results verify the effectiveness of the proposed control strategy.
Due to unfavorable factors, dangerous conditions occurred in the delivery of electric energy in Poland. This was the most serious incident of its kind since the 1980’s. Such a serious incident raised concern about the safety of the electric power system in the summer and led to the formulation of conclusions for the future. In this article, the author analyses the conditions, which caused that situation. Poland was experiencing a doubt in August 2015, which along with an extremely high maximum daily temperature created remarkably unfavorable conditions for power plants and decreased the capacity of overhead power lines. Such unfavorable metrological conditions occurred not only in Poland, but also in Central-Eastern and Western Europe. It is worth emphasizing that the safety of electric energy delivery was endangered only in Poland. The improper renovation and upkeep policies, as well as unplanned outages in power plants caused a significant decrease of available power in the National Electric Power System. Unscheduled flows between Germany and Poland ruled out the possibility of importing electric energy at such a critical time. The author presents the correlation between the maximum daily air temperature in the sweltering heat and an increase in the demand for electric energy. Overall, unfavorable conditions posed a threat in the delivery of electric energy in Poland. In this article, the author draws attention to the report from the Supreme Audit Office (Najwyższa Izba Kontroli – NIK) from 2014, which predicted such a dangerous situation. Unfortunately, that report remained unnoticed. The author formulated appropriate solutions in order to increase the safety of electric energy delivery in the summer and to prevent such occurrences in the future.
By means of small wind turbines, it is possible to create distributed sources of electricity useful in areas with good wind conditions. Sometimes, however, it is possible to use small wind turbines also in areas characterized by lower average wind speeds during the year. At the small wind turbine design stage, various types of technical solutions to increase the speed of the wind stream, as well as to optimally orientate it, can be applied. The methods for increasing the efficiency of wind energy conversion into electricity in the case of a wind turbine include: the use of a diffuser shielding the turbine rotor and the optimization of blades mounted on the turbine rotor. In the paper, the influence of the diffuser and rotor blades geometry on the efficiency of an exemplary wind turbine for exploitation in the West Pomeranian Province is investigated. The analyses are performed for three types of the diffuser and for three types of rotor blades. Based on them, the most optimal shapes of the diffuser and blades are selected due to the efficiency of the wind turbine. For the turbine with the designed diffuser, calculations of the output power for the assumed different values of the average annual wind speed and the constant Betz power factor and the specified generator efficiency are made. In all the analyzed cases, the amount of energy that can be generated by the turbine during the year is also estimated. Important practical conclusions are formulated on the basis of these calculations. In the final part of the paper, a 3D model of the wind turbine with the diffuser and rotor blades chosen based on earlier analyses is presented. As a material for the diffuser and rotor blades, glass fiber type A is applied. By means of calculations using the finite element method, the limit displacement of the turbine structure under the influence of a hurricane wind are determined. Based on these calculations, the correctness of the modelled small wind turbine structure has been demonstrated.
The article deals with the issue of the meaning of the Polish early education coursebooks for conservation/change in educational practices. It is the liberal and constructivist discourse to which the coursebook authors should refer (especially in the context of the present time and democracy) if these books are to become a tool of the prodevelopmental and emancipatory interest of both students and society. However, the research on Polish coursebooks for early education (grades I – III), show that this very condition has not been ful3 lled. In such a situation it is the German school coursebooks that might be inspiring because of their discursive background as well as of the methodological proposals and the range of content present in them. The article is also an attempt to reconstruct “the image of school” present in German early education coursebooks. It is possible to name and describe the key dimensions in this image such as: the democratic nature of teacher-student relations, the focus on the activation of students’ personal knowledge as well as on their ethical and cognitive autonomy, realistic vision of the world, trust in students’ competences, and creating the sphere of the nearest development.