Fast and accurate grid signal frequency estimation is a very important issue in the control of renewable energy systems. Important factors that influence the estimation accuracy include the A/D converter parameters in the inverter control system. This paper presents the influence of the number of A/D converter bits b, the phase shift of the grid signal relative to the time window, the width of the time window relative to the grid signal period (expressed as a cycle in range (CiR) parameter) and the number of N samples obtained in this window with the A/D converter on the developed estimation method results. An increase in the number b by 8 decreases the estimation error by approximately 256 times. The largest estimation error occurs when the signal module maximum is in the time window center (for small values of CiR) or when the signal value is zero in the time window center (for large values of CiR). In practical applications, the dominant component of the frequency estimation error is the error caused by the quantization noise, and its range is from approximately 8×10-10 to 6×10-4.
This article considers designing of a renewable electrical power generation system for self-contained homes away from conventional grids. A model based on a technique for the analysis and evaluation of two solar and wind energy sources, electrochemical storage and charging of a housing area is introduced into a simulation and calculation program that aims to decide, based on the optimized results, on electrical energy production system coupled or separated from the two sources mentioned above that must be able to ensure a continuous energy balance at any time of the day. Such system is the most cost-effective among the systems found. The wind system adopted in the study is of the low starting speed that meets the criteria of low winds in the selected region under study unlike the adequate solar resource, which will lead to an examination of its feasibility and profitability to compensate for the inactivity of photovoltaic panels in periods of no sunlight. That is a system with fewer photovoltaic panels and storage batteries whereby these should return a full day of autonomy. Two configurations are selected and discussed. The first is composed of photovoltaic panels and storage batteries and the other includes the addition of a wind system in combination with the photovoltaic system with storage but at a higher investment cost than the first. Consequently, this result proves that is preferable to opt for a purely photovoltaic system supported by the storage in this type of site and invalidates the interest of adding micro wind turbines adapted to sites with low wind resources.
A solar photovoltaic (PV) system has been emerging out as one of the greatest potential renewable energy sources and is contributing significantly in the energy sector. The PV system depends upon the solar irradiation and any changes in the incoming solar irradiation will affect badly on the output of the PV system. The solar irradiation is location specific and also the atmospheric conditions in the surroundings of the PV system contribute significantly to its performance. This paper presents the cumulative assessment of the four MPPT techniques during the partial shading conditions (PSCs) for different configurations of the PV array. The partial shading configurations like series-parallel, bridge link, total cross tied and honeycomb structure for an 8#2;4 PV array has been simulated to compare the maximum power point tracking (MPPT) techniques. The MPPT techniques like perturb and observe, incremental conductance, extremum seeking control and a fuzzy logic controller were implemented for different shading patterns. The results related to the maximum power tracked, tracking efficiency of each of the MPPT techniques were presented in order to assess the best MPPT technique and the best configuration of the PV array for yielding the maximum power during the PSCs.
An integrated Z-source inverter for the single-phase single-stage grid-connected photovoltaic system is proposed in this paper. The inverter integrates three functional blocks including maximum-power-point-tracking, step-up/down DC-side voltage and output grid-connected current. According to the non-minimum-phase characteristic presented in DC-side and the functional demands of the system, two constant-frequency sliding-mode controllers with integral compensation are proposed to guarantee the system robustness. By using two controllers, the effects caused by the non-minimum-phase characteristic are mitigated. Under the circumstance of that the input voltage or the grid-connected current changes suddenly, the notches/protrusions following the over-shoot/ under-shoot of the DC-bus voltage are eliminated. The quality of grid-connected current is ensured. Also, a small-signal modelling method is employed to analyze the close-loop system. A 300W prototype is built in the laboratory. A solar-array simulator (SAS) is used to verify the systematic responses in the experiment. The correctness and validity of the inverter and proposed control algorithm are proved by simulation and experimental results.
A sliding mode controller for the photovoltaic pumping system has been proposed in this paper. This system is composed of a photovoltaic generator supplying a three-phase permanent magnet synchronous motor coupled to a centrifugal pump through a three-phase voltage inverter. The objective of this study is to minimise the number of regulators and apply the sliding mode control by exploiting the specification of the field oriented control scheme (FOC). The first regulator is used to force the photovoltaic generator to operate at the maximum power point, while the second is used to provide the field oriented control to improve the system performance.The whole system is analysed and its mathematical model is done. Matlab is used to validate the performance and robustness of the proposed control strategy.
The energy efficiency of photovoltaic modules is one of the most important aspects in energetic and economic aspects of the project related to system installations. The efficiency of modules and the electricity produced by photovoltaic conversion in solar modules is affected by many factors, both internal, related to the module structure itself and its technical and external factors related to the energy infrastructure, which includes: cabling, inverters, climate conditions prevailing at the micro-installation location and the orientation and angle of inclination of the solar modules. The installation of photovoltaic modules should be preceded by an energy efficiency analysis, which will help to indicate the optimal solution adapted to the given conditions. The article presents a comparative analysis of the amount of energy produced under real and simulated conditions. Analyzes were made on the basis of research carried out in the Wind and Solar Energy Laboratory located at the AGH University of Science and Technology, data from solar irradiation data-bases and computer software for estimating energy resources. The study examined the correlation of the solar irradiation on the modules and the amount of electricity generated in the photovoltaic module. The electricity produced by the module was compared under real conditions and simulated based on two sources of data. The comparison and analysis of the amount of energy of the module were also made, taking simulated different angles of the module’s inclination into account.
The large variability and unpredictability of energy production from photovoltaic power microinstallations results from the dependence on the current weather conditions. These conditions depend on a number of factors and are variable over the time. Despite this specificity, photovoltaic micro-installations are becoming more and more popular in the world and in Poland. This is mainly due to the fact that the generation of energy from renewable sources has numerous advantages, the energy is free, renewable in time and ecological, and its production on its own gives partial independence from energy supplies from the power grid. In addition, the observed significant prices decrease of solar modules has further accelerated the development of the use of this energy source. Concern for this method of energy production among households has increased significantly in Poland after introducing the prosumer in the legal framework and the use of administrative and financial support. The implemented prosumer mechanisms allowed, for example, the net balancing of the energy consumed and produced by the micro-installation through storage in the power grid. The article describes the problem of balancing sources using solar energy, based on micro-installation used in the household (the so-called prosumer installation). The conducted analyses compared the load profile of a typical household and the energy generation profile from a photovoltaic installation, determining the real balancing formation level of such a system.
Recently, the search for new effective energy production solutions has been focused on the production of electricity using renewable and environmentally friendly carriers. This resulted in an increased interest in PV cells and cogeneration systems. The article looks at the main factors affecting their operational parameters against the background of the development history of subsequent generations of PV cells. Average daily solar radiation and wind velocity in Lodz were characterized. The research was done on a static and tracking system with a total peak power of 15 kWp and a 30 kW microturbine. PV panels are installed on the building of the Institute of Electrical Power Engineering of the Lodz University of Technology and they work as part of DERLab. A microturbine is inside the building. Energy measurements were carried out in 2016 giving grounds for the analysis of energy efficiency and financial analysis of the energy supply in buildings. Energy yields in the static and tracking system as well as percentage coverage of electricity from PV cells and microturbines were assessed. The distribution of monthly savings, annual savings of energy costs and the payback time of the investment costs of the systems subject to the test were determined. The research we have done allows us to say that the energy produced by follow-up modules is about 3 times greater than that generated in stationary modules. On the other hand, the annual savings of energy costs using gas micro-turbines are about 10 times higher than those of lagging panels. The analysis shows that it is possible to determine the profitability of the microturbine and photovoltaic panels use despite large financial outlays. The payback period of investment outlays is about 12 years when using the installation throughout the year.